602.3 Operable Parts.
Operable parts shall comply with 309.
602.4 Spout Height.
Spout outlets shall be 915 mm (36″) maximum above the finish floor or ground.
602.5 Spout Location.
The spout shall be located 380 mm (15″) minimum from the vertical support and 125 mm (5″) maximum from the front edge of the unit, including bumpers.
602.7 Drinking Fountains for Standing Persons.
Spout outlets of drinking fountains for standing persons shall be 965 mm (38″) minimum and 1090 mm (43″) maximum above the finish floor or ground.